Buy DIN VDE () Plugs And Socket-outlets For Household And Similar Purposes – Part 1: General Requirements On Fixed Socket-outlets from. Summary of testing: Tests performed: This test report complies with DIN VDE in conjunction with DIN VDE and. EK1 Find the most up-to-date version of VDE at Engineering
|Published (Last):||5 October 2014|
|PDF File Size:||18.15 Mb|
|ePub File Size:||5.68 Mb|
|Price:||Free* [*Free Regsitration Required]|
Affiliation List of ICS codes.
Live parts check protection inside the door and strengthen the protection of live parts socket can not touch with the probe. Bipolar plug with earthing contact insertion flanking force. With the device picture Certification of persons Do recognize your skills, register online to become certified.
May Number of pages: Test current with rated current – 16 A for portable socket outlet Temperature rise of terminals or connections on the additional function not exceed values of requirements of the relevant standards but not more than 70K. The impossibility of the contact of the single pole contact hole A. Electrical connectors and plug-and-socket devices – Connectors with thread coupling, water-protected, up to A – Part 2: Unipolar contact hole contacts not the possibility of B.
On both sides of the ground test. Thereafter the samples are cooled for the further tests below Tinsel cords or flexible cable with 0. Minimum opening width and minimum pull out force of contact jack. Legal notices Photo credits FAQ. BSgauge “go” gauge for plug Standard: Build your compilation Add to a compilation Add to a compilation create a compilation vve subscription wuthout subscription with subscription Build a watch list Add to the watch list.
The maximum pullout force plug 16d. If you have skype or whatsapp, pls tell me, we can chat more smoothly. The possibility of unipolar insertion plug including grams and grams 062-01 weight and the positioning rack.
Destruel Date of publication: The outer material by moulded plugs is totally removed when testing the supporting parts After this tests probe 4 must be possible to insert. Discover also Certification, assessment, diagnosis Get a quote for certification of systems, products or services, and vds certified. The maximum pullout force plug 16a.
To be quoted Packaging Details: Calibration Certificate Model Number: Caution the offer 1 user is reserved for a single user, any broadcast even 00620-1 his company is prohibited. Socket with PE and fixed connected plug is not allowed Register online at inter and intra-company training, and certifying diplomas, seminars, distance learning.
No bipolar plug ground contact can not be inserted. Terms and conditions for Customized compilation of standards Contact us Accessibility. Plugs and socket-outlets for household and similar purposes – Part More information add to basket. Cin test plug gauge. All other connections not exceed 45 K. Option to visualize changes at a glance.
AFNOR Editions Online Store
Select the first category of products searched and follow the instructions. Plugs and socket-outlets for household and similar purposes – Part 1: Terms and Conditions Terms of subscription Online watch.
Get a quote for certification of systems, products or services, and get certified. The maximum opening width of the contact jack. Purchase More information add to basket.
Test yourself or your business online. Socket R gauge 5.
DIN VDE Lehre 16e Socket Gauge with 18N
Code s Theme s Temperature rise on all other connections not exceed 45 K. After normal operation test of live parts check protection inside the door can not touch the probe.
To test the first time contact closure interval gauge. No water may penetrate in between the insulation and the strands 19 Temperature rise A plug 06220-1 inserted into the socket test current is passed into the socket for 1h Test current: Mounting, detail specification – Elektrische Steckverbinder und Steckvorrichtungen – Steckverbinder mit Gewindekupplung, spritzwasserdicht, bis A – Teil 2: Directly sin after while hot a pull test is conducted with 50N for 30s, The anchorage shall remain functional but displacement of the cord may exceed 2mm.
Fite Date of publication: Bipolar grounded plug diameter gauge and test equipment. January Number of pages: VG April Electrical connectors and plug-and-socket devices – Connectors with thread coupling, water-protected, up to A – Part 2: